Performing a life-cycle cost analysis (LCC) gives the total cost of a lighting system—including all expenses incurred over the life of the system. This analysis can be applied not only to lighting but for most of the appliances, automobiles, heating systems, and so on, when two systems are compared to determine the most cost effective options.
There are two reasons to do an LCC analysis:
- To compare different systems, or bulbs in this case.
- To determine the most cost-effective system or a bulb.
For some lighting systems, one of two situations may exist:
- The initial cost may be high but the energy costs will be low over its lifetime.
- The initial cost to buy a bulb or a system and the energy or the maintenance costs may be low, but the useful life of such a bulb or system may be short. (In this case, we may have to replace the appliance several times to get the same useful life as the other option.)
Therefore, a life-cycle cost (LCC) analysis can be helpful for comparing the total costs incurred over the lifetime of a lighting system. It is, in essence, calculating all the costs incurred to buy, maintain, and run the system over its lifetime.
In the formula above,
- Cost to buy is the purchase price of the bulb or the system.
- Cost to maintain is the cost incurred to maintain it in good operating condition. (For example in the case of a car, an engine oil change every 3,000 miles is part of maintenance costs.)
- Cost of energy is the energy or the fuel it takes to run the appliance or bulb for its lifetime.
- Replacement cost is the cost to replace the bulb. If bulb A has a life of 1000 hrs and bulb B has a life of 10,000 hours, then Bulb A needs to be replaced 10 times to get the same useful life period as that of bulb A. Therefore, 10 A bulbs need to be purchased for each Bulb B.
The table below shows a life cycle cost analysis in comparing an incandescent bulb and a CFL.
|Incandescent||Compact Fluorescent Light (CFL)|
|Rating||60 Watts||15 Watts|
|Lumen output||865 Lumens||900 Lumens|
|Cost to buy the bulb (\$)||\$0.60||\$5.00|
|Life of each bulb||1,000 h||10,000 h|
|Bulbs needed for same life||10 bulbs - \$6.00||1 bulb - \$5.00|
|Energy Consumption||60 Watts x 10,000 h
600,000 Wh = 600 kWh
|15 Watts x 10,000 h
150,000 Wh = 150 kWh
|Price of electricity||\$0.085||\$0.085|
|Cost of Electricity needed for 10,000 h||600 kWh x 0.085/kWh =
|150 kWh x 0.085/kWh =
|Total Cost (Life Cycle costs) to own and operate the bulbs for 10,000 h||\$51.00+\$6.00
Although they save energy, there are some disadvantages with CFLs:
- They are often physically larger than the incandescent bulbs they replace and simply may not fit the lamp.
- The light is generally cooler—less yellow—than incandescent light bulbs. This may result in less than pleasing contrast with ordinary lamps and ceiling fixtures. Newer models have been addressing this issue.
- Some types (usually iron ballasts) may produce an annoying flicker.
- Ordinary dimmers cannot be used with compact fluorescents.
- Like other fluorescents, operation at cold temperatures (under around 50–60 degrees F) may result in reduced light output.
- There may be an audible buzz from the ballast.